220.54. As specifically stated in the first sentence of this section of the Code, “The load for household electric clothes dryers in a dwelling unit(s) shall be either 5,000W (volt-amperes) or the nameplate rating, whichever is larger, for each dryer served.”
What is the demand factor for 9 household electric clothes dryer?
Table 220.54 Demand Factors for Household Electric Clothes Dryers
|Number of Dryers||Demand Factor (%)|
|12—23||47% minus 1% for each dryer exceeding 11|
How many amps does a 220 volt dryer use?
The Laundry closets are installed with a 220/240V power outlet that provides 20 Amps of power; this is intended for the dryer.
Is a dryer a continuous load?
Note the words maximum current (not just ‘turned on’!) and expected. Dryers and stoves and water heaters have elements that turn on and off, even while running.
How do you calculate service load?
Index: Loads. Feeders, Calculations = Annex D
- Go to annex D in your code book for reference. …
- Using your calculator multiply 2500 x 3 = 7500.
- Small appliance load = 3000.
- Laundry load = 1500.
- Using your calculator add 7500, 3000, 1500 = 12000 now subtract 3000 = 9000 now multiply by .35 = 3150 now add 3000 = 6150.
How do you calculate electrical load?
Compare the wattage of your air conditioner and furnace. Since you only use one at a time, add only the larger wattage rating to your equation. Divide the resulting number of watts by volts (most homes use 220 volts) to get the number of amps, or the electrical load.
How do you calculate demand load?
The demand load is the sum of the operational load (including any tactical load) and nonoperational demand loads. It is determined by applying the proper demand factor to each of the connected loads and a diversity factor to the sum total.
What is the maximum demand for a 14kW electric range?
The service demand load for one 14kW range is 8.8kW (See Figure 1). Regardless of the number, the first note applies if all the ranges are rated the same and are more than 12kW.
How do you calculate general lighting load?
General lighting and receptacle loads
Table 220.12 in the National Electrical Code considers a residence a listed occupancy at 3 VA per square foot; therefore, the general lighting load is determined by multiplying the square footage. For example, 2,800 square feet times 3 VA is 8,400 VA.
What is the feeder demand for one 15kw range?
The demand loads shown in Column C are for appliances with ratings 12kW, or less. The maximum load required for one 9kW range, when computing a service (or feeder), is 8kW.